- recommend products
- 7 Products
- Product Image
- Product Name
- FOB Price
- Model NO.: VIB-24
- Operation: Energy-storage Type
- Arc-extinguishing Medium: Vacuum
- Structure: ACB
- Type: Circuit Breaker
- Certification: VDE, ISO9001-2000, CE, CB, CCC
- Rated Current: 630/1250/1600/2000/2500/3150A
- Mechanical Endurance: 10000cycles
- Transport Package: Non-Solid Wooden Case for Export Shipment
- Origin: China Baoji
- Breaking Capacity: High Voltage Circuit Breakers
- Speed: Normal Type Circuit Breaker
- Installation: Withdrawable
- Poles Number: 3
- Function: Conventional Circuit Breaker
- Rated Voltage: 24kv
- Rated Frequency: 50Hz
- Trademark: Longxiang Electric
- Specification: IEC: M2-E2-C2
- HS Code: 85389000
Series of Indoor High Voltage Vacuum Circuit Breaker With Embedded Poles
VIB-24 series of Indoor High Voltage Vacuum Circuit Breaker with embedded poles is three phase A.C.50Hz indoor power distribution equipment with the rated voltage of 24kV.It's used for protecting and controlling the electrical equipment in the fileds of industry&mining enterprise,power plants and substation.
The main conductive circuit of this type vacuum circuit breaker with spring mechanism is embedded pole,that can greatly improve the reliability of insulation,mechanical and breaking performance,and really realize the free-maintance and longer mechanical&electrical life.
This type Vacuum Circuit Breaker conforms to national standards and the stipulations of IEC standard.The capability reaches grade of M2-E2-C2.
The products is used for many kinds of switchgear like KYN28-24(GZS1)and can be fixed installation.
Applying ambient conditions
2.Ambient humidity:the average humidity of a day should be no more than 95%;the average humidity of a month should be no more than 90%.
3.Earthquake intensity:not exceed 8 degrees.
4.Saturated vapour pressure:the average pressure of a day should be no more than 2.2kPa;the average pressure of a month should be no more than 1.8kPa.
5.The height above sea level:1000m(besides the special requirements).
6.It should be installed in the places without fire,explosion,serious filth,chemical erosion and violent vibration.