- Model NO.: VS1-24
- Operation: Electric Type
- Arc-extinguishing Medium: Vacuum
- Structure: ACB
- Type: Circuit Breaker
- Certification: VDE, ISO9001-2000, CE, UL, CB, CCC, IEC
- Rated Current: 630/1250/1600/2000/2500/3150A
- Mechanical Endurance: 10000cycles
- Brand Name: Longxiang
- Specification: IEC: M2-E2-C2
- HS Code: 85389000
- Breaking Capacity: High Voltage Circuit Breakers
- Speed: High-Speed Circuit Breaker
- Installation: Withdrawable
- Poles Number: 3
- Function: Circuit-Breaker Failure Protection
- Rated Voltage: 24kv
- Rated Frequency: 50Hz
- Insulated Cylinder: Epoxy Resin
- Trademark: Longxiang Electric
- Origin: China Baoji
Series of Indoor High Voltage Vacuum Circuit Breaker with Common Insulated Cylinder
VIB-24 series of Indoor High Voltage Vacuum Circuit Breaker with Common Insulated Cylinder is three-phase A.C.50Hz indoor power distribution equipment with the rated voltage of 24KV.It's used for protecting and controlling the electrical equipment in the fileds of industry & minning enterprise,power plants and substation.This type Vacuum Circuit Breaker conforms to national standards and the stipulation of IEC standard,the capability reaches grade of M2-E2-C2.
The product adopt composite insulation way,spring charged operation and screw rod push mechanism, with the characeristics of small volume,compact design and reliable operation, it can easily match with the switchgear and meet the "Five Preventions"demands.
This kind of Vacuum Circuit Breaker can be used for many kinds of switchgear like KYN28-24(GZS1),This series of products include:VCB truck,isolation truck and fuse truck etc.
Applying ambient conditions
2.Ambient humidity:the average humidity of a day should be no more than 95%;the average humidity of a month should be no more than 90%.
3.Earthquake intensity:not exceed 8 degrees.
4.Saturated vapour pressure:the average pressure of a day should be no more than 2.2kPa;the average pressure of a month should be no more than 1.8kPa.
5.The height above sea level:1000m(besides the special requirements).
6.It should be installed in the places without fire,explosion,serious filth,chemical erosion and violent vibration.