- Model NO.: ZN85-40.5
- Operation: Electric Type
- Arc-extinguishing Medium: Vacuum
- Structure: ACB
- Type: Circuit Breaker
- Certification: ISO9001-2000, CE, CCC
- Material: Epoxy Resin
- Specification: IEC: M2-E2-C2
- HS Code: 85389000
- Breaking Capacity: High Voltage Circuit Breakers
- Speed: Normal Type Circuit Breaker
- Installation: Open Frame
- Poles Number: 3
- Function: Conventional Circuit Breaker
- Rated Voltage: 40.5kv
- Trademark: Longxiang Electric
- Origin: Baoji Shaanxi China
Truck Type Indoor High-voltage Vacuum Circuit Breaker
ZN85-40.5/T type indoor high voltage indoor vacuum circuit-breaker is used for switchgear KYN6140.5(Z),it is most new type of power supply and distribution equipment.This product is accordance with GB1984-2003 stand.This series include:Vacuum circuit breaker truck,isolation truck and fuse truck.
1.This vacuum circuit breaker adopts compound insulation;it can meet air distance and creepage under normal run condition,and it effectively reduce the dimension of VCB,the overall arrangement is reasonable and simple,with aesthetic appearance.
2.The operating mechanism is especially newly designed for this VCB,the outlet curve has good adaptation with requirements of vacuum interrupters.It has high reliable with characteristics of long life and easy maintenance and free-maintenance for operating mechanism.
3.This truck adopts screw rod nut push-in mechanism whitch can realize easy pushing-in or pushing-out from panel,compulsive mechanical interlock way is adopted,meet the"Five Preventions"function;suitable for varies sit and the working sites which have rigorous run condition.
Applying ambient conditions
2.The height above sea level:≤1000m(besides the special requirements).
3.Relative humidity:the average humidity of a day should be no more than 95%;the average humidity of a month should be no more than 90%.
4.Saturated vapor pressure:the average pressure of a day should be no more than 2.2kPa:the average pressure of a month should be no more than 1.8kPa.
5.Earthquake intensity:not exceed 8 degrees.
6.It should be installed in the places without fire,explosion,serious filth, chemical erosion and violent vibration.
Following information is required for order
Ω 1.For VCB
Full type name,rated current,rated short-circuit breaking current.
Rated voltage of operating circuit
The switchgear with or without earth switch
Name and quantity of spare parts and components
Other special requirents for VCB.
Ω 2.Isolation switch
Full type name and rated current
Ω 3.For fuse
Full type,name and quantity.
Type and quantity of fuse
Is enquipped with surge arresters and discharge counter
For special requiremtne,please consult with manufacturer.